By the end of June 2017 , our client in Saudi Arabia we had completed and exported a RO water treatment project with total capacity of 10TPH(240tons per day)BWRO system plant , which is RO reverse osmosis water system with raw water from municipal tap water ( TDS ? 500mg / L) to produce output water used for bottled water .
In order to satisfy our client’s requirement, our Conhoo’s engineer designed the technological process with MMF + ACF + RO system + UV. Firstly, Raw water from municipal tap goes into the refined quartz sand filter to remove rust, sediment, colloidal and other large impurities in the water. Then water goes through the activated carbon filter to get rid of odor, organic matter, colloid, iron and chlorine; it also has a good effect at reduction of water turbidity and chroma, purification lower pollution for the follow-up system. Then the water, in turn, goes through the 5?m security filter and the reverse osmosis system, increases the pressure of HP pump to 1.0-1.6MPa. Finally , fresh water is produced with TDS?10mg/L?25??under this pressure.
The advantages of this system are capable of continuous purified water production by manual operation or automatic operation, with online water quality monitoring instruments. It’s a stable, safe and reliable purified water producing system.
On the other hand, we also provide the bottled water machine upon request by our client and exported together for on site installation in Saudi Arabia. Our Conhoo’s engineer, will attend the installation site to implement installation and commissioning for this 10TPH BWRO system plant and bottled water machine.
To reward our client’s trust and support to us as well as long term cooperation in future, it is our responsibility to ensure the whole system running successfully and smoothly.
Dnfoss High Pressure Pump
Please Tell Us Your Water Problem Here
We Would Like To Provide The Technical Solution.